DC 0079 - Frequency Changes during Large Disturbances and their effect on the total system - Phase 2
As of 1 October 2017 Grid Code Modifications GC 0036 and GC 0079 have now been superseded by Distribution Code Modification DC 0079.
Please note: all documents on the Grid Code GC 0079 web page will remain accessible as an archive to this new Distribution Code website area. As of 01 October 2017 all new documentation for Modification DC 0079 will only be available on the Distribution Code website. Access to the GC 0079 web page can be found here - http://www2.nationalgrid.com/UK/Industry-information/Electricity-codes/Grid-code/Modifications/GC0035-GC0079/
DCRP DC 0079 working group - Terms of Reference
REPORT TO AUTHORITY
Report to Authority 1 - 4 December 2017
The purpose of
this Report is to assist the Authority in its decision to implement the proposed
modifications to the Distribution Code and Engineering Recommendations G59. The
proposed modifications were subject to industry consultation in August 2017. Responses
from this consultation show that the industry is in favour of these
The Distribution Code Review Panel recommended that modifications are made to the Distribution Code and Engineering Recommendations G59 to ensure that all embedded generators with a commissioning date on or after 1 February 2018 comply with the following:
- That where rate of change of frequency (RoCoF) protection is used as Loss of Mains protection, the applied setting should be 1Hzs-1 with a definite time delay of 500ms.
- That all generation using discrete relays (non- type-tested) as part of their loss of mains technique should demonstrate stability for appropriate RoCoF and vector shift disturbance
- That vector shift protection technique should not be used as Loss of Mains protection for generators using discrete relays as part of loss of mains protection scheme.
DECISION OF AUTHORITY - 15th December 2017
The Authority has approved this modification. Full details of Ofgem's decision can be found in their decision letter which can be found here. The resultant modifications to the Distribution Code and Engineering Recommendation G59-3/3 will become effective from 1 February 2018.
DC 0079 OPEN LETTERS
Open Letter 1 - 30 October 2017
Open Letter 2 - 13 December 2017
WORK GROUP MEETINGS
Work Group Meeting Dates 2017
Minutes and actions