2018 Stakeholder Workshops
DC 0079 - Frequency Changes during Large Disturbances and their effect on the total system - Phase 2
As of 1 October 2017 Grid Code Modifications GC 0036 and GC 0079 have now been superseded by Distribution Code Modification DC 0079.
Please note: all documents on the Grid Code GC 0079 web page will remain accessible as an archive to this new Distribution Code website area. As of 01 October 2017 all new documentation for Modification DC 0079 will only be available on the Distribution Code website. Access to the GC 0079 web page can be found here - http://www2.nationalgrid.com/UK/Industry-information/Electricity-codes/Grid-code/Modifications/GC0035-GC0079/
DCRP DC 0079 working group - Terms of Reference
Reports to Authority
REPORT TO AUTHORITY
|Approved by the Authority, Awaiting Implementation|
The Distribution Code Review Panel - email@example.com
It is recommended that the Distribution Planning Code and EREC G59 should be changed to ensure that all existing embedded generators make changes to comply with the following:
All non-type-tested embedded generators with plant rated >16A per phase commissioned before 1 February 2018
|Working Group||DCRP DC0079 Working Group|
The Distribution Code public consultation sought views from industry stakeholders on the modification to both the ‘DCode’ and Engineering Recommendation (EREC) G59 and EREC G83. It was published on the 31 January 2018 with a deadline for responses by 23 February 2018.
|Report to Authority|
Following the meeting of the Distribution Code Review Panel (the Panel) held on 7th February 2019, it was agreed that the Report to Authority would be amended with minor changes before submission of the Report to Authority for approval. The Panel agreed to this submission and that the modification proposals better facilitate the objectives of the Distribution Code.
|The Authority has approved DCRP/MP/18/08 - Report to Authority - DC0079 Frequency Changes during Large Disturbances and their Impact on the Total System on 05 August 2019 with an implementation date of 01 September 2019.|
DCRP/MP/18/08 - Authority Decision
Report to Authority DC0079 (Phase 2) - 27 March 2018
The purpose of this report is to assist the Authority in its decision to implement the proposed modifications to the Distribution Code Engineering Recommendations G59 and G83. The proposed modifications were subject to industry consultation in August 2017 and February 2018. During the August Consultation no response was received from manufacturers of type tested plant. As a result a second consultation was undertaken in February 2018 and one response was received from a type tested plant manufacturer. The manufacturer did not object to the proposal but proposed a delay in the implementation date.
It is recommended that modifications be made to Distribution Code and Engineering Recommendations G59 and G83 to mandate that all type tested generators commissioned on or after July 2018, demonstrate stability for appropriate RoCoF and vector shift disturbances. The report recommends:
a) That the rate of change of frequency (RoCoF) criterion used for Loss of Mains protection must be 1 Hzs per second with a definite time delay of 500ms
b) That vector shift protection technique should not be used as Loss of Mains protection for type tested generators and that generation must not trip for vector shifts of up to 50º
c) That type tested generation includes stability tests to prove immunity to RoCoF and vector shift less than the above criteria.
REPORT TO AUTHORITY
Report to Authority DC0079 (Phase 1) - 4 December 2017
The purpose of this Report is to assist the Authority in its decision to implement the proposed modifications to the Distribution Code and Engineering Recommendations G59. The proposed modifications were subject to industry consultation in August 2017. Responses from this consultation show that the industry is in favour of these modifications.
The Distribution Code Review Panel recommended that modifications are made to the Distribution Code and Engineering Recommendations G59 to mandate that all non type tested embedded generators with a commissioning date on or after 1 February 2018 comply with the following:
- That where rate of change of frequency (RoCoF) protection is used as Loss of Mains protection, the applied setting should be 1Hzs-1 with a definite time delay of 500ms.
- That all generation using discrete relays (non- type-tested) as part of their loss of mains technique should demonstrate stability for appropriate RoCoF and vector shift disturbance
- That vector shift protection technique should not be used as Loss of Mains protection for generators using discrete relays as part of loss of mains protection scheme.
DECISION OF AUTHORITY - 15th December 2017
The Authority has approved this modification. Full details of Ofgem's decision can be found in their decision letter which can be found here. The resultant modifications to the Distribution Code and Engineering Recommendation G59-3/3 will become effective from 1 February 2018.
2017 Meeting Dates
Q1- What is DC0079
A1- DCRP Mandated WG